This software utilizes publicly available and commonly used dissolved gas analysis (DGA) method for transformer fault diagnostics purposes, Duval Triangles (IEC 60599, Annex B).
Customer acknowledges and agrees that Vaisala shall not assume any risk or liability in connection with the use or application of the diagnostics data by the Customer or any other user of such data. The use and/or application of any such data shall be at the sole risk and liability of the Customer or the user.
|DGA Diagnostics is an optional feature and requires a license. Contact Vaisala for acquiring the license.|
DGA Diagnostics page shows the progression of selected data points from the past year overlaid on top of Duval triangles:
- Triangle 1: Classic Duval triangle for DGA in oil-filled transformers using methane, ethylene, and acetylene
- Triangle 4: Diagnosis of low-temperature faults in oil-filled transformers using hydrogen, methane, and ethane
- Triangle 5: Diagnosis of low-temperature faults in oil-filled transformers using methane, ethylene, and ethane
DGA monitor automatically selects the data points according to criteria described in section Criteria for data points in DGA diagnostics. The data points are listed in a table below the triangles. Clicking a table row highlights the data point in the overlay and displays the gas ratios as percentages.